Selecting I/O Units
I/O units typically are referred to as local or remote, a reference loosely interpreted to mean distance. I like to think of local as directly (or nearly directly) connected core processor peripherals. PCI- and ISA-enabled peripherals are good examples of local devices. A remote I/O unit usually has some kind of communication medium, such as a serial (RS-232 or RS-485) cable, wireless, infrared, Ethernet, FireWire or USB (to name a few). These remote interfaces have devices that may connect to the local core processor of the controlling computer but modify the data in such a way that it is transferred via another medium to its destination. This medium acts as an extension cord that extends the distance from the core processor bus to the device. This distance may be as short as a meter or as long as kilometers.
Remote vs. local I/O is important when considering the expense of additional cables to a control location. If I were to design a local control system using a set of PCI I/O cards, every point of I/O would have a cable installed. Consider a 1,000-point system with 1,000 cables. Just imagine the expense if an electrical contractor quoted an installation cost of $100 US per cable (the total would be $100,000 US)! In such a case, remote I/O allows a single wire such as CAT 5 (Ethernet) to be run to distributed I/O units. While 1,000 cables are still required for installation, the signal cable distance is shorter, decreasing the labor and materials cost of installation. In more unusual projects I've worked on, remote I/O implementation also provided incredible savings in cable weight. In one project, I recall estimating that we saved approximately 1,000kg of mass by just converting the system to remote I/O.
Shorter sensor and effector cables routed to a nearby I/O unit also are easier to test, debug and maintain. For example, if the cables run through a complex vehicle such as a ship or an airplane, a suspected wire failure might require physical cable tracing. If the wire length is 500 meters, each meter of wire may require inspection. If an I/O unit is located next to sensors and effectors, the communication media cable from the control computer to the I/O unit is still 500 meters, but it may be an Ethernet fiber bundle. The sensor and effector cables to the I/O unit may be only meters long. Clearly, debugging a couple of meters of wire is easier than several hundred meters.
Analog signals also may be affected by electrical noise, which places additional and undesirable signals into the analog data. Devices switching on and off may cause electrical noise. Power cables too close to sensitive signals also may create anomalies in I/O unit readings. Typically, the shorter the wire, the lower the probability of receiving electrical noise. Digital media cables such as copper Ethernet are susceptible to electrical noise too. Digital media typically employs a method of data validation that detects when data corruption occurs, but it still can be a problem.
Nonmetal technologies such as fiber are not susceptible to noise because they use light and not electrons. When installing a system it is useful to perform a site survey to evaluate potential sources of electrical noise. Plan for cables to be a significant distance from high-energy cables (power conductors, RF transmitters and so on) and high-energy systems (such as anodizing systems, high-voltage switching equipment and high-energy control hardware).
Modularity is all about selecting channels or points of I/O. While most I/O units support either all digital points or all analog points, some support both types. Mixed systems, as we call them, allow the designer to pick a single unit and select all the points required. As most systems require both analog and digital points, mixed I/O units optimize the cost-effectiveness of the design and reduce size and weight.
In addition, modularity improves life-cycle maintenance. An I/O unit with removable points may require a few seconds to replace a component and restore system operation. Replacing an entire I/O unit is much more costly in labor and downtime. Modularity also allows smaller, cheaper components to be stocked as spares should a replacement be necessary, also reducing downtime.
|PostgreSQL, the NoSQL Database||Jan 29, 2015|
|HPC Cluster Grant Accepting Applications!||Jan 28, 2015|
|Sharing Admin Privileges for Many Hosts Securely||Jan 28, 2015|
|Red Hat Enterprise Linux 7.1 beta available on IBM Power Platform||Jan 23, 2015|
|Designing with Linux||Jan 22, 2015|
|Wondershaper—QOS in a Pinch||Jan 21, 2015|
- PostgreSQL, the NoSQL Database
- Sharing Admin Privileges for Many Hosts Securely
- HPC Cluster Grant Accepting Applications!
- Internet of Things Blows Away CES, and it May Be Hunting for YOU Next
- Ideal Backups with zbackup
- Wondershaper—QOS in a Pinch
- Designing with Linux
- Red Hat Enterprise Linux 7.1 beta available on IBM Power Platform
- Slow System? iotop Is Your Friend
- January 2015 Issue of Linux Journal: Security
Editorial Advisory Panel
Thank you to our 2014 Editorial Advisors!
- Jeff Parent
- Brad Baillio
- Nick Baronian
- Steve Case
- Chadalavada Kalyana
- Caleb Cullen
- Keir Davis
- Michael Eager
- Nick Faltys
- Dennis Frey
- Philip Jacob
- Jay Kruizenga
- Steve Marquez
- Dave McAllister
- Craig Oda
- Mike Roberts
- Chris Stark
- Patrick Swartz
- David Lynch
- Alicia Gibb
- Thomas Quinlan
- Carson McDonald
- Kristen Shoemaker
- Charnell Luchich
- James Walker
- Victor Gregorio
- Hari Boukis
- Brian Conner
- David Lane