Monitoring Your UPS With apcupsd
When you have a UPS that is powering more than one computer, and you want to protect every computer from power failures, you can configure apcupsd to work as network master/slave service. Listing 3 and 4 describe how to configure apcupsd as master and a slave in order to shut down both in case of a power failure.
The master apcupsd is configured as described above in stand-alone configuration, with the exception that the configuration directive NETACCESS is now true and the master will use port 6666 to communicate with slaves. The apcupsd master will connect to the slave at my.network.slave.com in order to communicate alerts and power events. The slave apcupsd shares the same configuration except that instead of using the serial port, it will listen to my.network.master.com to get all the information needed to operate correctly.
apcupsd configuration is very flexible. But adding to this flexibility, you can also configure your control scripts to execute customized actions, and you can even configure your UPS eeprom to suit your needs.
When apcupsd detects anomalies from your UPS device, it will make some decisions that usually result in one or more calls to the script located in /etc/apcupsd/apccontrol. The apccontrol file is a shell script that takes the first argument that apcupsd passes to it to do actions. These actions are set up by default to sane behavior for all possible situations apcupsd is likely to detect from the UPS. Nevertheless, you can change the apccontrol behavior for every action. To do so, simply create a file with the same name as the action you want to customize, which is passed as the first argument (argv, or $1 for shell scripts). Place your script in the /etc/apcupsd/ directory. The arguments that apccontrol can recognize are shown in Table 3.
If, for example, you want to write your own routine for the on-battery action, you can write your own shell script, as shown in Listing 5, called onbattery and put it in the /etc/apcupsd/ directory. Doing so will run the customized script before the default action. In case you don't want the default action to be taken, terminate your customized script with an exit code of 99. If you want to write customized scripts to replace the default behavior, you are encouraged to edit the apccontrol script and at least mimic its behavior in your own script. Please be aware that writing faulty scripts may cause your system to crash during power failures.
In SmartUPSes there are at least 12 different values stored in the eeprom that determine how the UPS reacts to various conditions such as high line voltage, low line voltage, power down grace periods, etc.
In general, for the moment, it is not recommended to change eeprom values unless absolutely necessary. There have been several reported cases of problems setting the Low Transfer Voltage. Consequently, if at all possible, do not attempt to change this value.
If, despite these warnings, eeprom vales must be changed, we recommend to connect your UPS to a Windows machine running PowerChute and making the changes.
In the absence of alternatives, eeprom values can be changed also with apcupsd. Before doing so, it is recommended that you make a printed copy of UPS parameters as they are before any eeprom changes, so that they can be checked against the changes made. This can be done by printing a copy of the output from apcaccess status and also of the output from apcaccess eprom.
Once this is done, choose which eeprom values you want to change. Choose the new values from the list provided by apcaccess eprom. For the battery date, and the UPS name, you can use any eight characters.
To make the eeprom changes with apcupsd you must first stop the apcupsd dæmon. See “Stopping Apcupsd” in the appropriate section of apcupsd manual. Then edit the appropriate configuration directive in /etc/apcupsd/apcupsd.conf.
It is recommended to change one eeprom value at a time, by defining only one configuration directive at a time. After each change, check that everything is okay before proceeding to the next value you wish to change.
To actually change the eeprom, as root with the apcupsd dæmon stopped, enter:
When it has completed the reprogramming of the eeprom, it will print the new STATUS report. Check that you got the expected results before continuing.
- Handling the workloads of the Future
- Readers' Choice Awards 2014
- diff -u: What's New in Kernel Development
- How Can We Get Business to Care about Freedom, Openness and Interoperability?
- December 2014 Issue of Linux Journal: Readers' Choice
- Synchronize Your Life with ownCloud
- Non-Linux FOSS: Don't Type All Those Words!
- Days Between Dates?
- Computing without a Computer